Non-ASME DHW Stock Storage Tanks, 80-115 Gallon
Storage tanks are required in conjunction with WH water heaters. The heater provides rapid heating of a small volume of water; the tank provides a storage medium with enough capacity to handle short-term loads.
Under ASME section IV part HLW rules, an
ASME-compliant tank is not required when the total system volume does
not exceed 120 gallons, or when the total heating capacity does not
exceed 200,000 BTUH.
When properly selected and installed, these tanks can provide 80% draw without appreciable temperature decrease in a single-temperature application.
- Available in 80 and 115 sizes
- 150 PSIG maximum working pressure
- Two magnesium anodes included
- Glass-lined * Steel jacketed
- Insulated with rigid foam to R12.9, meets ASHRAE 90.1
- 2 NPT connections for heater piping and tank outlet
- Ports for T&P valve, tankstat, thermometer, and drain valve