Under ASME section IV part HLW rules, an ASME-compliant tank is not required when the total system volume does not exceed 120 gallons, or when the total heating capacity does not exceed 200,000 BTUH.
Our stainless steel tank provides high volume and resistance to erosion without any lining to fail.
When properly selected and installed, these tanks can provide 80% draw without appreciable temperature decrease in a single-temperature application.
- 150 PSIG maximum working pressure
- No anodes required
- No lining required
- R18 Insulation
- 2 NPT connections for heater piping and tank outlet
- Side ports for T&P valve, tankstat, thermometer, and drain valve
- Indoor/outdoor installation